Get Gorman-Rupp Pumps 12B20-B 1340494 and up Owner's manual. Get all Gorman-Rupp Pumps. Priming centrifugal. The following are used to alert maintenance per. Thank You for purchasing a Gorman‐Rupp pump. Read this manual carefully. And Maintenance manual is designed to. Enclosed impeller, self‐ priming centrifugal. Gorman-Rupp Pumps 86A2-F3L 1330589 and up User Manual. And Maintenance manual is designed to help you achieve the best. Self-priming centrifugal model.
80 SERIES OM−00955 PAGE I − 1 INTRODUCTION INTRODUCTION Thank You for purchasing a Gorman-Rupp pump. Read this manual carefully to learn how to safely install and operate your pump.
Failure to do so could result in personal injury or damage to the pump. This Installation, Operation, and Maintenance manual is designed to help you achieve the best performance and longest life from your Gorman- Rupp pump. This pump is an 80 Series, semi-open impeller, self- priming centrifugal model with a suction check valve. The pump is designed to be close-coupled to a Deutz diesel engine. The pump is designed for handling most non-vola- tile, non-flammable liquids containing specified en- trained solids.
The basic material of construction for all wetted parts is gray iron and steel. If there are any questions regarding the pump or its application which are not covered in this manual or in other literature accompanying this unit, please contact your Gorman-Rupp distributor, or: The Gorman-Rupp Company P.O. Box 1217 Mansfield, Ohio Phone: (419) 755−1011 or: Gorman-Rupp of Canada Limited 70 Burwell Road St. Thomas, Ontario N5P 3R7 Phone: (519) 631−2870 For information or technical assistance on the en- gine, contact the engine manufacturer’s local dealer or representative.
Because pump installations are seldom identical, this manual cannot possibly provide detailed in- structions and precautions for every aspect of each specific application. Planmeca Pm 2018 Manual. Therefore, it is the re- sponsibility of the owner/installer of the pump to ensure that applications not addressed in this manual are performed only after establishing that neither operator safety nor pump integrity are com- promised by the installation. Pumps and related equipment must be installed and operated ac- cording to all national, local and industry stan- dards. The following are used to alert maintenance per- sonnel to procedures which require special atten- tion, to those which could damage equipment, and to those which could be dangerous to personnel: Immediate hazards which WILL result in severe personal injury or death. These instructions describe the procedure re- quired and the injury which will result from failure to follow the procedure. Hazards or unsafe practices which COULD result in severe personal injury or death.
These instructions describe the procedure required and the injury which could result from failure to follow the procedure. Hazards or unsafe practices which COULD result in minor personal injury or product or property damage. These instructions describe the requirements and the possi- ble damage which could result from failure to follow the procedure. NOTE Instructions to aid in installation, operation,and maintenance, or which clarify a procedure.